G&W Electric’s Capnut Terminations are designed and tested in accordance with IEEE-48, 1975 standards for Class 1 terminations. They are used where insulated cables are connected to generators, switchgear, transformers, overhead lines or sectionalizing equipment.
Features and Benefits
Single conductor units in ratings of 15, 25, 34.5, and 46kV for 1/0 to 2000 kcmil cables.
Three conductor units are rated 15, 25, and 34.5kV for conductor sizes through 1000 kcmil.
Bracket and flange mount models for pole or equipment mounting.
Accepts any construction of extruded dielectric, paper insulated or armored cable.
Ratings Chart for Capnut Terminations
|Current Rating||Same as cable||Same as cable||Same as cable||Same as cable|
|1 minute dry, ac (kV)||50||65||90||120|
|6 hour dry, ac (kV)||35||55||75||100|
|10 second wet, ac (kV)||45||60||80||100|
|15 minute dry, dc (kV)||75||105||140||170|
Accessories Chart for Capnut Accessories
|1 or 3 Conductor||3 Conductor||1 or 3 Conductor||3 Conductor||3 Single Conductors||3 Single Conductors|
|1 or 3 Conductor||3 Conductor||3 Single Conductors||3 Single Conductors|
|High mole Polyethylene and Kerits||1 or 3 Conductor MAY REQUIRE TUBE SEAL||3 Conductor MAY REQUIRE TUBE SEAL||3 Single Conductors MAY REQUIRE TUBE SEAL||3 Single Conductors MAY REQUIRE TUBE SEAL|
|Flat Steel Armored||3 Conductor||3 Conductor||1 or 3 Conductor|
|Interlocked* Armor||3 Conductor|
|Wire Armor||3 Conductor||3 Conductor||1 or 3 Conductor|
|Type CCE Split Conduit Extension Adaptable||√||√||√||√||√||√||√||√||√|
|*Application on cable with a solid jacket under the armor. For cables with a jacket over the armor, a cable entrance fitting combination (DP3-EE-EE-GL-ACC-DP-1) can be used.|
|Aerial Lugs Accessories include: Style 3-D Clamp style, Style 8 Bertial 4 hole and Style 18 Horizontal Bus style|
|Novoid Accessories include: Novoid A and Novid X for use with PILC Cable, Novoid A and Novoid 224 for use with XLPE/EPR.|
|Novoid 224 not applicable with PILC Cable. Novoid X not applicable with XLPE/EPR.|